The date of payment from buyers deliver within days
Intersection of Jingquan Road and Fenghua Street, High-tech Development Zone, Xinxiang City, Henan Province, China
1) Improving the winding impact distribution
2) High anti short circuit ability
3) High mechanical strength
4) Strong cooling capacity.
1) Rated capacity: 630~31500KVA
2) High Voltage Winding: Multi-cylinder type or cake structure
3) Low Voltage Winding: Drum or spiral structure
4) Core: Quality cold-rolled silicon steel.
1) Applicable to 3 phase, 50HZ ,35kv or less
2) Industrial mining enterprises
3) Industrial and agricultural distribution and power and lighting.
1.Magnetically controlled reactor is through the DC bias magnetic core to change the magnetic permeability of the core to achieve inductor adjustable, and with a fixed capacitor, automatic controller, etc. constitute a dynamic reactive power compensation system to achieve Power compensation capacity stepless adjustment, the reactive power compensation to achieve the best results.
2. To improve the power factor of the power grid, you can make the power factor of 0.9 ~ 0.99 requirements; and reduce the loss and reactive power loss, energy saving, suitable for power system huge network loss is very serious users.
3. Eliminate harmonic pollution, improve the safety factor of the power grid system, improve the voltage stability of the power grid and transmission line transmission capacity.
4. Stable end voltage (to prevent the voltage is too high or too low), improve the transformer and transmission lines and other electrical equipment life.
5. For the user expansion, in many industries to install MCR-type magnetic reactor reactive reactive power compensation device, can achieve 1.2 to 1.5 times the expansion, substantial savings in expansion costs.
6.CarR type magnetically controlled reactor SVC dynamic reactive power compensation system cost-effective, compared to domestic TCR-type SVC low price 1/3.
7. Magnetic control reactor by the air gap core, coil, fuel tank, radiator, oil conservator, casing, according to the size of the pressure relief valve, gas relays, thermometers and other major components, both pressure , Gas, temperature protection device.
8. Reactor application of computer software to optimize the design of technical performance parameters, the performance indicators in line with national and industry standards and user needs.
9. Magnetically controlled reactor has the characteristics of compact structure, low loss, low temperature, low noise, small volume, light weight, flame retardancy, moisture resistance, simple installation and maintenance. And meet the non-oil (non-polluting) requirements of the substation, distribution site use, energy saving and environmental protection is the ideal product.